GSHP for Grade II House in Royston
This 200 year old property was converted from an Oil fired boiler to a high efficiency ground source heat pump on Boreholes
- Date: Feb 2019
- Client: Mr & Mrs Newman
- Project Type: Grade II Listed
About this Project
Mr & Mrs Newman wanted to future proof their property and stop importing fossil fuel heating oil. The new heating system involved the following
- 270m2 5 bedroom property
- 3 boreholes, depth of 110m through 6 differnet types of challenging geology, clay, gravel, flint, chalk, green sands , mudstone sands
- 500 Litre Unifresh Hot water/combination buffer cylinder – hygiencially fresh hot water
- 14kW ground source heat pump
- Loft insulation (RHI requirement)
- Solid walls unchanged
- Single glazed windows unchanged
- No floor insulation
- Gov’t RHI Renewable Heat Incentive £35,489 over 7 years
Following the installation the Client was very please and wrote this notice and review of our work. The notice remains on the wall for passers-by and church goes to learn more about renewable heating with heat pumps and how our designs for grade 2 listed properties enable them to switch away from the fossil oil grid
Phase 1 Drilling
The Drilling process took 7 days from start to finish with a 12 Ton rig and full mud treatment unit to keep the site tidy the boreholes where then connected back into the boiler room and pipework electrofusioned a thte joints nad manifold, follwed by pressure testing pipework and flushing with biocide
Phase 2 Heat Pump and Unifresh Tank Installation
The oil boiler was removed and disposed of, the heat pump and 500L Unifresh hot water tank & heating buffer were installed and commissioned.
The existing radiators were not allowed to be changed due to the listing of the building, however, the heat pump runs on weather compensated heating curves for efficiency and comfort and the property is heated very well in what is a very cold part of Hertfordshire with temperatures dropping to -5degs during winter. Ground Suns design of the whole system allows for properties like these to be heated all year round. With the correct engineering approach hard to heat properties with no insulation and single glazing are made sustainable for the future
Ground Sun installs ground source heat pumps for this 'harder to heat' farmhouse in rural Essex It's a myth that heat pump technology is not suited to older, harder to heat properties. If the heat pump is correctly designed and sized this technology works efficiently...
Ground Source Heat Pump for new build house in East Sussex Ground Sun have designed, supplied and installed a GSHP and underfloor heating with passive cooling for this spectacular 350m2 new build. Two 120m boreholes were drilled and header pipe laid from the...
Water Source Heat Pump for Riverside Cottage Ground Sun installed a water source heat pump system for this beautiful riverside cottage in Hertfordshire. Two Ochsner GMSW 7 plus heat pumps were installed in cascade to provide 100% of the space heating and hot water...
Ground Sun wins the 2017 Small Scale Project of the Year - for its project at Eton Manor Rugby Club - at the National Energy Efficiency Awards. The awards were held at the Hilton Metropole Hotel in Birmingham and were presented by Lenny Henry! Judges considered the...
Ground Sun are delighted to have won the RHI Installer of the Year award at the Greater London Energy Efficiency & Healthy Homes Regional Awards. The awards were held at Lords Cricket Ground on Wednesday 24th May 2017 and have been developed to recognise and...